RAISED FLOOR ACCESSORIES
|Ventilation panels with swirl diffusers||Cool air from under the raised floor enters the room via swirl diffusers to regulate the ambient temperature in the room. Drafts are avoided thanks to the swirling movement of the air at the outlet.
Also available as perforated row ventilation plates or steel ventilation plates with flow control.
|Ventilation panels||Full-steel ventilation panels, 600 x 600 mm, air flow of 15%, 24% or 38% (incl. flow control).|
|Suction lifters||Suction lifters to lift floor panels (with wall mounting or storage container).|
|Panel attachment||Panels screwed to substructure from underneath. Screwing the panels from above is not necessary.
Some panels are provided with quick release for easy access.
|Stairs||Any number of steps, made of the selected panel material, with aluminium fascia top trim.|
|Railings||Railing made of galvanised square tube 40 x 40 x 2 mm, with 2 knee rails|
|Cavity barriers||Vertical barrier for raised floor in specified height, made of selected panel material.|
|Blanking panel||To close the gap between switchboard base frames and standard raised floor panels.|
|Skirting||PVC core skirting (60 x 10 mm).|
|Subfloor sealant||Single component – resin-based emulsion paint floor sealant.|
|Swirl diffusers||Swirl diffuser diameter 150 or 200 mm , incl. dirt trap and adjustment ring, flow rate approx. 50 m3 / h.|
|Service outlets||Ackermann service outlets, without equipment, incl. panel cut-out and covered hinged lid|
|Transformers rails||Transformer rails comprising two square tubes 40x40x2 mm, incl. raised edges made of flat steel 40×5 mm, galvanised (only compatible with Kalthoff-System K1060PB)
Transformer weight max. 2.5 T
|Fire resistance F30-AB||Upgrading of the aforementioned raised floor to fire resistance class F30-AB in the area of escape routes. Upgraded substructure and panels made of reinforced mineral fibre (A2), non-combustible.|
|Temporary floor panels||Installation of temporary floor panels (28 mm ) during electrical installation and removal at a later date, incl. disposal and replacement with the original panels.|
|Hardboard floor panels||Hardboard 3.0 mm to protect the panels during construction. Boards laid on butt joints and fixed with adhesive tape. Disassembly and disposal on site.|